Originally Posted by huckabeecj
Hey Guys Im new to this site so forgive me. I have a Dewalt code reference book. One part is minimum wire ampacity for a package heat pump. Here are the details
Model:acesre6333 serial 4242424
ac volts 208/230 ph 1 hertz 60
volt max 253 min 197 min circ amp 22.1
com pressor rla 14.5 lra 82 fuse max amps 35
cond motor fla 1.6 hp ¼ charge 164
blower motor fla 2.4 hp 1/3
factory test psig low side 150 high side 300
circ breaker amps 30
this equip suitable for outdoor use only
when installing one of the heat kits permanently identify the model on this name plate
model vac ph # 1 #2 kw
khjgc 240 1 60 9.5
mop max overcurrent protection
I get the 90 amp breaker result, but for the minimum wire ampacity the come up with 79.3 amps. Dose anyone get that?
I'm not following you.The a/c has a minimum circuit ampacity of 22.1 and a max breaker of 35. Size your wire to the 22.1 and you should be good.
Without seeing which strip is in the unit a 30amp breaker may be correct.