Intersystem grounding lug
I've avoided them, but the AHJ wants one on a service change and relocated panel and meter. I saw one hanging out of the meter box on #6 copper looking like an afterthought and I'm wondering how others are handling this requirement for residential services. Seems to me, the lug can be installed on the exposed GEC between the house and the rod, but I'm remembering that mess hanging out of the meter box.
Another new service down the street either doesn't have one or I sure can't find it. Aren't they supposed to be easily located?
I still think the first guy needing it should install it, but I guess the code thinks otherwise.