Hi, my boss is doing a load calc and existing load center schedule. He is using a template an inspector gave to him. It has blanks for connected load and demand load and we need help figuring out the difference. In the sample problem they have different values. Thanks guys
ElectricianTalk.com - Are you a Professional Electrical Contractor? If so we invite you to join our community and see what it has to offer. Our site is specifically designed for you and it's the leading place for electricians to meet online. No homeowners asking DIY questions. Just fellow tradesmen who enjoy talking about their business, their trade, and anything else that comes up. No matter what your specialty is you'll find that ElectricianTalk.com is a great community to join. Best of all it's totally free!
The topics covered on this site include activities in which there exists the potential for serious injury
or death. ElectricianTalk.com DOES NOT guarantee the accuracy or completeness of any information contained
on this site. Always use proper safety precaution and reference reliable outside sources before attempting any construction or remodeling
the connected loads are all the loads that are installed. the demand load is the amount that article 220 says you need to use to do the load calc (different parts of 220 allow you to use a demand for several loads of same type that are not going to be running simultaneously and continuously, depending on the occupancy and the types of loads)
If you are going to sit back on your laurels and armchair quarterback the NEC, you will always be 3 years too late. Start threads now for the next code cycle proposals and do something about it
The Following User Says Thank You to wildleg For This Useful Post:
you can also do peak demand on occasion based on the highest reading from poco at the property address to overrule your calculated demand sometimes. I did it once to keep an existing 400 amp service instead of having to bump up to a 600 amp. (calc was 408 amps but peak was only 225 amps).