Originally Posted by jewalker88
My local AHJ stated that 110v outlet for gas range can't come off of the micro/range hood cir. I can't find a code to suport that. anyone have any Ideals?
Did you rough-in your range hood to be cord connected? Article 422.16 says that if your range hood is cord connected, it has to meet certain conditions. One of them is that range hood needs to be on and individual branch circuit (dedicated).
As far as the range hood/microwave oven argument, I think if it is located above the range and part of it's function is a range hood, it should follow the rules for range hoods.