Originally Posted by Gamit
From my understanding you need a disconnecting means at least 5 foot away but within sight 680.12. Which means my disconnecting means could be as far as 50' away"within sight" correct? But how far is the receptacle need to be 6' to 20' away 680.22 (A)(3) or not less then 6' and not exceeding 10' 680.43 (A) ? Im thinking the 6' to 20' because the other may be implying indoor installation only.
Always been my understanding and OSHA/Local Inspector interpretation, line of sight no matter what the conditions or 5' away.