Adding 30amp 240v receptacle for laser in a Operating Room
We have a customer purchasing a portable laser to be used in an OR. Specs call for an L6-30R receptacle. The existing LIM does not have the capacity to supply this load. Mfgr calls for GFI protection. Partner wants to run a 10-3 HG MC cable to the critical power load center and install a Line Guard GFI module at the receptacle location.
They do not make HG 30amp twist locks and will this comply with 517-19 (H)?
This is a small "Surgicenter" facility.
Sent from my SM-G930V using Tapatalk
The Following User Says Thank You to robertselectric9 For This Useful Post:
ElectricianTalk.com - Are you a Professional Electrical Contractor? If so we invite you to join our community and see what it has to offer. Our site is specifically designed for you and it's the leading place for electricians to meet online. No homeowners asking DIY questions. Just fellow tradesmen who enjoy talking about their business, their trade, and anything else that comes up. No matter what your specialty is you'll find that ElectricianTalk.com is a great community to join. Best of all it's totally free!
The topics covered on this site include activities in which there exists the potential for serious injury
or death. ElectricianTalk.com DOES NOT guarantee the accuracy or completeness of any information contained
on this site. Always use proper safety precaution and reference reliable outside sources before attempting any construction or remodeling
Surgical lasers have long been connected using receptacles that are not "hospital grade" because no suitable ones existed. The older arc-lamp YAG lasers usually required 50A 3ph and every facility seemed to use a different standard receptacle for them. However, I'd say the code does require that the receptacle be HG listed. Failure of the laser may not kill the patient, but it would be disastrous to have it stop working partway through a surgical procedure. I'd make the owner/engineer answer this question and sign off on a specific part number for it.