ElectricianTalk.com - Are you a Professional Electrical Contractor? If so we invite you to join our community and see what it has to offer. Our site is specifically designed for you and it's the leading place for electricians to meet online. No homeowners asking DIY questions. Just fellow tradesmen who enjoy talking about their business, their trade, and anything else that comes up. No matter what your specialty is you'll find that ElectricianTalk.com is a great community to join. Best of all it's totally free!
The topics covered on this site include activities in which there exists the potential for serious injury
or death. ElectricianTalk.com DOES NOT guarantee the accuracy or completeness of any information contained
on this site. Always use proper safety precaution and reference reliable outside sources before attempting any construction or remodeling
1) If you have a "thin bond wire" within your armored cable, you are dealing with AC cable, not MC. The only MC with a LARGE, bare, aluminum conductor is MCI-A (aka - Southwire MCAP or AFC MC-STAT)
2) All HCF cable needs to be terminated with fittings specifically listed for use with said cable.
3) The thin bonding strip can either be wound around the outside of the armor and clamped in the fitting, OR it can be cut flush with the armor. It is not designed to be terminated under a separate bonding screw. If you have a push on fitting, the strip should be cut flush with the armor so that it doesn't interfere with the grip fingers of the fitting.
4) Don't forget to install the redhead insulators in the end of the armor before terminating the AC cable onto a fitting.
The Following User Says Thank You to LJSMITH1 For This Useful Post: