Type B LED Tube New Revolution: Double-end powered, meet UL/ETL Type B certification
SA8.19 Risk of electric shock – relamping
SA8.19.1 As specified in Clause SA6.13.2, devices substituting for linear fluorescent lamps shall be evaluated for a possible risk of electric shock while installing, removing, or replacing the LED lamp device.
SA8.19.2 One end (lamp base) of the device under test shall be connected to its intended source of supply while the other end (lamp base) of the device shall be considered accessible and shall be connected to the shock hazard measurement meter circuit and, in turn, to earth ground as shown in Figure SA8.1. The current shall not exceed 5 M.I.U (7.07 peak M.I.U.).
SA8.19.3 The construction of the shock hazard measurement meter circuit, meter, and the explanation of M.I.U. measurement unit are described in UL 935.
ElectricianTalk.com - Are you a Professional Electrical Contractor? If so we invite you to join our community and see what it has to offer. Our site is specifically designed for you and it's the leading place for electricians to meet online. No homeowners asking DIY questions. Just fellow tradesmen who enjoy talking about their business, their trade, and anything else that comes up. No matter what your specialty is you'll find that ElectricianTalk.com is a great community to join. Best of all it's totally free!
The topics covered on this site include activities in which there exists the potential for serious injury
or death. ElectricianTalk.com DOES NOT guarantee the accuracy or completeness of any information contained
on this site. Always use proper safety precaution and reference reliable outside sources before attempting any construction or remodeling