Do the test at 250V initially to check anything connected, then disconnecting/bypassing any current/voltage using equipment on the circuits.
When testing each circuit separately, disconnecting the circuit under test from the MCB removes the RCD from the test!.
But on a global test at 500V L-E, L-N, N-E, how do you bypass/disconnect the RCD in a split load consumer unit?
Do you disconnect the tails from the incoming side of the RCD and connect to the outgoing side of the RCD, (same with the 2nd RCD on a split load)? Using the outgoing side of the RCD to connect the tails to the busbar?
Do you disconnect the tails from the incoming side of the RCD and connect to the busbar with ie: a croc clip.
Other option is to leave everything connected and test from the outgoing side of the RCD (RCD open) and test those RCD circuits globally and the same with the second RCD if split load?
ElectricianTalk.com - Are you a Professional Electrical Contractor? If so we invite you to join our community and see what it has to offer. Our site is specifically designed for you and it's the leading place for electricians to meet online. No homeowners asking DIY questions. Just fellow tradesmen who enjoy talking about their business, their trade, and anything else that comes up. No matter what your specialty is you'll find that ElectricianTalk.com is a great community to join. Best of all it's totally free!
The topics covered on this site include activities in which there exists the potential for serious injury
or death. ElectricianTalk.com DOES NOT guarantee the accuracy or completeness of any information contained
on this site. Always use proper safety precaution and reference reliable outside sources before attempting any construction or remodeling