Latest REC solar modules and "smudges" under the glass
Has anyone out there had experience with solar modules from REC having marks on them that look like a grease mark but turn out to actually be under the glass due to a manufacturer defect? The solar company that I work for in New England has seen a few dozen of these. Some have installed them for customers who don't care about asthetics. However, my concern is that these defects could actually cause problems in the future. I'v seen some string inverter systems have problems with constantly throwing arc fault errors and some happen to have REC mods on them. I'm wondering if there could be a connection with these "smudges" and electrical noise on the system. What do you all think?
ElectricianTalk.com - Are you a Professional Electrical Contractor? If so we invite you to join our community and see what it has to offer. Our site is specifically designed for you and it's the leading place for electricians to meet online. No homeowners asking DIY questions. Just fellow tradesmen who enjoy talking about their business, their trade, and anything else that comes up. No matter what your specialty is you'll find that ElectricianTalk.com is a great community to join. Best of all it's totally free!
The topics covered on this site include activities in which there exists the potential for serious injury
or death. ElectricianTalk.com DOES NOT guarantee the accuracy or completeness of any information contained
on this site. Always use proper safety precaution and reference reliable outside sources before attempting any construction or remodeling
We haven't used REC mods lately. As far as the arc-fault codes go:
- are you using Solar Edge inverters?
- are you megging all your DC conductors after the array has been bonded to the EGC?
- do the arc fault codes follow the inverter or the strings?
- are your homeruns direct (no splice) between the strings and the inverters?
- if there are splices, are you changing from #10 to #8 using a touch safe photovoltaic connector (mc4)?