I am installing a new service at my home. The service is a buried 150' aluminum cable (supplied by the electric company) that will come at the the end to a meter. From the meter is runs about 4' over to a Switch panel with a main breaker. The problem I'm having is that Victoria Electric says I can't use aluminum wiring from the Meter box to my Switch panel. I've pulled out the aluminum wiring (3/0 for the hot and 2/0 for the nuetral) and am preparing to put in copper, however everything I read says it's not against code to use the aluminum wiring. This is costing me roughly $160 to switch out just because they say the aluminum is not permitted. What is the clarification (i.e., VEC Code) on this?
ElectricianTalk.com - Are you a Professional Electrical Contractor? If so we invite you to join our community and see what it has to offer. Our site is specifically designed for you and it's the leading place for electricians to meet online. No homeowners asking DIY questions. Just fellow tradesmen who enjoy talking about their business, their trade, and anything else that comes up. No matter what your specialty is you'll find that ElectricianTalk.com is a great community to join. Best of all it's totally free!
The topics covered on this site include activities in which there exists the potential for serious injury
or death. ElectricianTalk.com DOES NOT guarantee the accuracy or completeness of any information contained
on this site. Always use proper safety precaution and reference reliable outside sources before attempting any construction or remodeling
Thanks for posting on ElectricianTalk.com. The Moderators/Admin of this forum would prefer if you post Do It Yourself related topics on our sister site www.DIYChatroom.com
As stated in the sign up page, ElectricianTalk.com is designed for electrical industry professionals to discuss issues and topics related to the electrical trades and related industries. Many of our professionals are also members at DIYChatroom.com and are looking forward to assist you with your needs.