Been looking threw cec can’t find where is talks about xp connectors on teck. Question is when you are running teck from xp area to a non xp area are xp connectors required on both sides or just hazardous area side? And where does it state this?
I am tasked with designing electrical controls/automation/instrumentation cabinets and field wiring to instruments in hazardous locations like class I Zone 0, 1, and 2 (div 1 and div 2).
In general, wiring and devices need to be rated for the environment (hazardous location) they are in...