Makes sense, the ATS is the first means of disconnect and N is bonded to G there, so it must not be bonded anywhere else.I just got called from an inspector that inspected a generator install that I did. I had to separate the grounds and neutrals in the main panel since it now a sub panel after installing a service rated ATS.
He's probably full of **** but it might but seeing as he caught a real mistake I might just go along and run the jumper.He said since I added a ground bar in the panel I needed to run a jumper to the other bar. I asked him why and he said it changed in the 2017 but could only tell me its' in 250 somewhere!:vs_mad:
Clean this up. I can't figure out what you've posted.
Are you telling us that your gen-set is fundamentally different than Poco power?