Is it still legal to double up 2 or 3 grounds under a lug in a panel? I know the neutral isn't allowed anymore like that.
The CH panels you use don't have holes in the tub to install ground bars? An $8 ground bar can solve all of your grounding terminal woes.Hmacanada said:You are talking about bond screws right ? If you are .. Not sure about all panels but the ones I use(C/H) don't have enough spaces to separate all the bonds. I'm one of the bad guys here though . I,ll twist 4 or 5 together on a new tie in. Sent from my iPhone using electriciantalk.com
it is legal only if the panel has a listing for more than 1 wire under a terminal.Maybe I'm a little too evil about it
Sent from my C5215 using electriciantalk.com mobile app