I'm hoping someone can shed some light on 230.85 Emergency disconnecting means. I saw this the other day..with a 3 wire going into the main panel located inside with grounding conductors and grounded conductor bonded. Something tells me this is not correct with the labeling??? Any help would be appreciated thank you.....this is a job my buddy is working on...he is licensed as well.
1.1 MB Views: 100