I am dealing with this on a job for a contractor of mine and I'm getting a lot of heat (because he has an antiquated electrical system and its my fault . you know the type) the problem is Im having trouble finding out anything. I got the jest of it and the fact that the ground and the 3rd phase are one in the same but go to different areas .And that I cant fuse the grounded phase in a distribution situation. What I don't get is why I have wacky amp readings like (phase A 73amp /phase B the grounded leg has 93 amps and the phase 3 has 83 . Its not the motor I swapped phases on that to rule it out . The motor is a 25 hp 3 phase and at 240 v should draw 65 amp. WTF
John I started at the line side of the starter and went to the load . I swapped phases A & C then C & B to keep the rotation . Tomorrow is another day and I will post some more results then , meanwhile if you have any other ideas please share . thanks
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!