Ok, so we get a mandatory windfall of work every three years thenThere is no such thing as grandfathered in......lol.
I'm in! :thumbup:
Would it be just as safe with two services from the same pole then...?I believe it would be a lot safer if this was wired as a sub panel. You have a ground rod but no ground wire back to main panel. I say that's a no no. Sell a new sub those stab locks look like a problem Waiting to happen. Good luck
One problem though, the panel isn't balanced. There's 5 circuits on one leg and 3 on the other.View attachment 35545 this panel is 3 wire feed . There is a rod at location with 6awg attached, in field now per 230 this is ok I believe . No metal between buildings plastic gas line....Nec 2011 cycle in this local, this is viewed as separate service correct. Advise thanks . This out building is a garage.