A building outside light MH 347 volt (canadian) connectted directly to circuit breaker (24 hours). I couldn't find any timer for 347 volt circuit DPST.
In electrical room there isn't any 120 volt panel.
I found a Photocell from Lumatrol for 347 volt, but beside that, can I wire in electrical room in a box with relay contactor and a transformer for 120 volt timer or some otherway.
Thanks randomkiller and BryanMD for your quick respond.
Actually, I have two circuits each 5x 70W MH. Installing just a 347 volt photocell in each circuit make the job done. But If I have to use a timer DPST for 347 volt circuit which I can't find, I have to use a Transformer 347volt to 120 volt or lower as you said 24 volt to get timer hooked up and a 2-pole contactor with 120 or 24 volt coil. (Well it is easier to work in electrical room than working outside installing photocells, but the cost would be much higher). Summary I think I will go with photocell (347 volt 3 wires), just I have to find the feed where is accessible outside to cut and put a junction box.
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!