I have recently finished a kitchen and have had trouble with Halo 4 inch recessed LED and my 15 amp arc fault circuit. I have performed the usual troubleshooting and have found nothing unusual. I have connected the circuit to a non afci circuit breaker and the breaker holds and the lights work fine. But when I am connected to the afci c.b. the breaker trips the moment the lights are turned on. Is it possible that one of the led trims is causing the problem?