I make all the electrons line up for their Flu shots
Replaced the arc fault breaker? Megger the circuit wiring yet? Test swap the arc with a gfi breaker and put load on the circuit?Sorry if this has been discussed already but has anyone used an arc fault tester that finds the arc fault. We have a house that keeps tripping but we cant find the problem even after taking all the devices out.
Checked the service entrance wiring? (l just fixed an afci trip issue when I upgraded the service and had the poco redo the drop attachment splices. )
50/50 chance the problem is the breaker and not the wiring.