Replaced the arc fault breaker? Megger the circuit wiring yet? Test swap the arc with a gfi breaker and put load on the circuit?Sorry if this has been discussed already but has anyone used an arc fault tester that finds the arc fault. We have a house that keeps tripping but we cant find the problem even after taking all the devices out.
ground wire touching a neutral?Yea we figured it out. Something simple i just posted to soon. The job is a little ways away so i just wanted to have some ideas other than what i usually try.
Neutrals tied in together from dif circuitsdrspec said:ground wire touching a neutral?
that will do itNeutrals tied in together from dif circuits
Well then, I guess afci's made an electrician out of you. I too am more careful of how I make up multigang boxes, and always double check outlets to make sure the ground is not contacting neutral. Afci's have made an electrician out of me.that will do it
I remember doing that 12+ years ago when we first started using those god awful things