I would like to clarify something. - When I was trained we used to install cadet type heaters (fan forced) with single pole thermostats. Is this really code compliant? I am taking on on-line CEU course and it looks like it might not be. (I do not know the hp of the fan unit... (I could check on that.) Anyway, I had an inspector recently tell me that I needed to use two pole thermostats. (That would be the required disconnect.) However, up until that inspector said that was what he wanted I had been using single pole. - Does anyone else have any input on this? Thanks in advance.