hotblueelectric· Rolling Thunder
Discussion Starter · #1 ·
Ok let me see if I have this right. I'm running (2) 120 volt circuits 375 feet for two gate openers that use 12 amps starting and 8.5 amps running. I will be installing (2) # 4's on 20 amp circuit breakers, and (1) #10 neutral and one #10 ground. All in pvc. This should keep my voltage drop to 2%. Do these calculations look correct. Any comments are appreciated.