Discussion Starter · #1 ·
Would anyone know what the required spacing is for emergency lighting in a hallway for a multifamily building in New York City?
I guess NYC HUD..I'm not certain about NYS HUD..IslandGuy said:NYC HUD or NYS HUD?
Note the exceptions, though. The requirements may be completely different for dwelling units and sleeping units in Groups I-1, R-1, R-2 and R-3.1006.2 Illumination level.
The means of egress illumination level shall not be less than [2 foot-candles (22 lux) at the floor level in exits, at exit discharges, and in public corridors, and shall not be less than 1 foot-candle (11 lux) at the floor level in exit access components other than public corridors] 1 foot-candle (11 lux) at the walking surface level.