If this is for a facility use the one in the 70E (You have read the 70E right?)Does anyone have a Hot work permit that I can look at for Arc Flash Policy?
OK so you are a facility and have to do something internal and also deal with outside contractors right?I do have the NFPA 70E book, however I was trying to create one that would serve both contractors and the maintenance personnel here.
Thanks for the word document.
Should have used the 1584 , much more accurate and your Ei's would be lower.Sorry, i should told you I have been working on our Facility compliance with Arc Flash. I preformed the survey, made the one line drawings, and preformed the calculation per NFPA 70E.
You don't want one that covers both, keep them seperate.I am now fininshing the policies and the training procedures for our facility. I am looking for a Hot Line permit that will cover our maintenance personnel and I follow the outside contractors work. I would like to have one that covers both.
If you did an analysis you should have Ei's not HRC's, you don't want to mix the analysis results with the HRC's/.I facility has decided that we will not work on it Hot. however we need to be able to verify that there is nothing present. We have Category 0-4 hazard.
You are making your guys wear a 40 cal suit for every thing? GOod luck with that.I have a 40 cal/cm2 suit that our qualified people will wear when verifying that voltage is not present.
There is no such thing, every PPE garment I have seen marked HRC 0 are counterfit.I am purchasing Category 0 jackets for all of our maintenance personnel who we are qualifying.
This will help (See attachment)I am just trying to make sure I did not over look something.