The Specs for the WH03242 are HERE.
They show voltage as 120V -- not 240V and not 120/240V
Download the Manual and you'll see the 30amp outlet is:
"120V, 30A RV – NEMA TT-30R
A maximum of 26.7 Amps current may be drawn from this receptacle."
His generator has a maximum wattage of 3,200 running watts - 4,000 peak. Specs say 26.7 amps at 120 volt = 3,204 watts,
This generator is undersized.
My microwave is 1,550w, toaster 900w, coffee maker 1,500w = 3,950 watts and we haven't added a furnace blower motor, refrigerator, freezer, lighting, etc.
When I install a Reliance GenTrans, I always recommend 7,500 watt generator minimum with a 30 amp, 120/240v twist lock.
Using the 10 circuit GenTran, you could turn off all circuits except one or two and try that.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!