I just had a rough inspection on a new house, its a HUD house and they wanted code minimum so i ran 1 15a circuit for the fridge, range hood, and a single ceiling fixture (max 2 60w lamps). Inspector failed me for it saying fridge needs its own circuit. The 2 SABCs are there, ive never heard of such a thing as a required fridge only circuit, just that it cant be on the SABC. im pretty sure its not in the code. its a easy fix, receptacle is 3' from the panel and im not going to make a fight out of it but i say BS. what do you guys say?