I just finished a kohler 20 resa install with a RXT 100 amp transfer switch/load center. While doing the initial settings on the generator control board i hit auto to clear a setting and the generator tried to start. I'm in nyc where the utility delivers 208 volts and i realized that @ 240 volts the transfer switch was detecting an outage. I changed the vr voltage on the generator to 210 but its still trying to start. Can anyone with experience with these tell me what else,i believe on the transfer switch i have to do to get my utility and gen voltages to match. I called my local authorized dealer who i have installed for in the past and he wants $550 for a start up fee. I'd hate to have to pay that because i'm missing something simple. Obviously this is the first time i tried to start it on my own. Any help would be greatly appreciated!