Good evening all, failed inspection today for having only one duplex receptacle on a countertop in the laundry room. Inspector wants 2’ 4’ rule. He’s citing 210.52 (C), I strongly believe this only applies to the items listed in that code. It’s my opinion he reads “similar areas” and thinks the laundry room qualifies. I think the code is trying to stay in food prep areas of the home. Thoughts? We are going to challenge the city tomorrow on this.