I have a 3phase 4 wire 120/208 panel fed from a transformer that is fed from a 277/408 panel. We turned it on and while testing voltage at a receptacle, it read 60v. I won't be back to trouble shoot til Tuesday but I can't stop thinking about it. Two explanations that I could think of is a loose neutral, or insufficient bonding of the neutral to ground from the xfmr. What are your opinions on these theories?
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!