I confused here
For 480-600V 3 phase car wash equipment motors using NEC D8 to size breaker and fused disconnect
which calc I use 125% max. Or 175% max
And minimum of 110%. If one of my motors was 10 FLA @480-600V
1 - 1 of 1 Posts
This is an older thread, you may not receive a response, and could be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!