Nec 422.12 says that i can run a permanently connected air conditioner off of the 60 amp branch feed to the heat strip in this furnace. So how would you guys do this? Do you come out of the furnace with the 10/2 cable or from a small breaker panel hooked to the 60? Do I just wire nut the 10 inside the air handler to the 6 gauge and take it to a fused disconnect outside? How would you do it? I'm trying to get around fishing an almost impossible 10/2 line to the panel. Thanks.