Hi all, I am just curious. I have taken state license test and I remember one questions asking me about outside lighting being covered under what Nema specification in category I or II or 4. Anyone know the answer?
Well if it meant the type of enclosure the light had to be in....
EDIT: damned table looked fine when I pasted it in... (I'm cleaning it up now)
1General-purpose.Protects against dust, light, and indirect splashing but is not dust-tight; primarily prevents contact with live parts; used indoors and under normal atmospheric conditions.
2Drip-tight. Similar to Type 1 but with addition of drip shields; used where condensation may be severe (as in cooling rooms and laundries).3 and 3SWeather-resistant. Protects against weather hazards such as rain and sleet; used outdoors on ship docks, in construction work, and in tunnels and subways.3RIntended for outdoor use. Provides a degree of protection against falling rain and ice formation. Meets rod entry, rain, external icing, and rust-resistance design tests.
4 and 4XWatertight (weatherproof). Must exclude at least 65 GPM of water from 1-in. nozzle delivered from a distance not less than 10 ft for 5 min. Used outdoors on ship docks, in dairies, and in breweries.
5Dust-tight. Provided with gaskets or equivalent to exclude dust; used in steel mills and cement plants.
6 and 6PSubmersible. Design depends on specified conditions of pressure and time; submersible in water; used in quarries, mines, and manholes.
7Hazardous. For indoor use in Class I, Groups A, B, C, and D environments as defined in the NEC.
8Hazardous. For indoor and outdoor use in locations classified as Class I, Groups A, B, C, and D as defined in the NEC.
9Hazardous. For indoor and outdoor use in locations classified as Class II, Groups E, F, or G as defined in the NEC.
10MSHA. Meets the requirements of the Mine Safety and Health Administration, 30 CFR Part 18 (1978).
11General-purpose. Protects against the corrosive effects of liquids and gases. Meets drip and corrosion-resistance tests.
12 and 12KGeneral-purpose. Intended for indoor use, provides some protection against dust, falling dirt, and dripping noncorrosive liquids. Meets drip, dust, and rust resistance tests.
13General-purpose. Primarily used to provide protection against dust, spraying of water, oil, and noncorrosive coolants. Meets oil exclusion and rust resistance design tests.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!