Looking for an idea to code compliantly fix this, I installed a 100amp disconnect in an old westinghouse piece of switchgear and after installing the disconnect there is a 1/4" gap between the disconnect and metal cover . Does anyone have any ideas how to cover this up easily? thanks
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!