You gotta have a single main effective with the 2020.This is my new tempole i just set up 06/06/22. And inspector left note that “service disconnect”
Can anyone help me correct this pole?
Thank a lot
Iowa granted an small extension to continue using the old temp services.
But all the new stuff needs the main.
Install a NEMA 3R (outdoor) breaker panel with a main breaker.
QO or Homeline 100a, 12s runs around 135-140/e at the big box stores.
Better yet, if you just use a meter/main such as the Milbank product, you have your meter socket, main breaker, and eight spaces all in one box. Few boxes mean lower install labor.