I agree with the above posts, but what the OP is asking seems to be an install that is more and more requested, "a flat screen above a tub/spa/hot tub/Jacuzzi, etc.
Gotta be some way to do the install and be code compliant. Seems like 680.43(A) can be worked around if not a "general-purpose branch circuit", but 680.43(A)(1) seems to stop any receptacle from a least 6ft. from a tub.
Hate to run a cord exposed to a code compliant receptacle.
How about a hard wire install?