I've installed heat trace on interior pipes in the past bit not the roof style, my question is can you extend a the length by connecting two together as long as you don't exceed the amperage rating of the Supply wiring or do you void the UL listing by doing this?
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!