Hmmm. Well - I have not been in the States for very long and come from Europe where a situation like this will get a house officially buttoned up by the police. This kind of "spagetti" and open end wiring is not code where I'm from.
Glad to hear that it is "OK" here though... :laughing::laughing:
Good god almighty that's some sloppy crap. Bonus points on the last photo however for the disconnects nailed to a chunk of wood @ a 45° angle. Love the split bolt just chillin there as well. I laughed when I saw this mess for real
actually yes a long time ago i had to fix some diy messes in a bar and found a couple hot wires splices together with just a 1/4 by 20 bolt ,nut and washers
not even taped up (fluorescent lights in a drop ceiling)
found a few other things that made me shake my head!
the new bar owner is a friend of mine and called me to check things out before he had the poco turn the power on (smart call):laughing:
This is an older thread, you may not receive a response, and could be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!