SE cable is rated for service entrance and has a UV resistant jacket. It states that it can be used from the service drop to the meter socket. Are we allowed to strip the jacket off the wire where the wires connect to the service drop? Are the individual wires rated for exposure to sunlight? Or just the jacket? Thanks.