If the cable has pulled out of the connector and needs to be repaired, such as with settling when ran underground, I've installed either a conduit nipple or a length of conduit to a coupling then re-cut in the cable... For an armor and outer rubber repair, nothing I can think of off hand..
Contact the wire manufacturer and they can give you their method of repair that will still give you the same classification rating. Just had to repair a cable in some tray here. 2 layers 88 2 layers 33 and a huge piece of split shrink for a boot.
1 - 4 of 4 Posts
This is an older thread, you may not receive a response, and could be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!