Rest In Peace
So use the AHJ as your 'stick' A~shockDuplex.
One side is up and running with a tenant. HO tried to get power turned on for the other side.
AHJ wrote up.
1. Replace service riser
2. Replace meter can.
3. Repair ground rod connection.
4. Remove exposed romex and non 3R rated box.
bonding bridge goes in today. I did not quite finish yesterday. I have the exposed uf to still pipe into the panel. I will probably have to crawl under the house.If I cared, I'd say something about:
A PVC upper strapped like chit
Not seeing the intersystem bonding bridge
The holes from the old straps not being caulked