Is it allowable to put the generator automatic transfer switch before the service disconnect? 230.82 talks about circuits for standby power
I did not install this it was on a generator I have a maintenance contract. I was going to check to see if the transfer worked so I turned off service disconnect when nothing happened I opened up the disconnect to find it was after the transfer switch.Sounds like you did it wrong ! You need service rated ATS.