Discussion Starter · #1 ·
Doing a 200 amp service with the t box in the basement , the 4 gang meter socket will be outside, panels inside . The inspector said he wants a disconnect between tbox and meter . So my question is from the load side of the disconnect do i run seu or ser to meter socket ? And if I do need ser do they have a isolated neutral kit for the meter?