MWBC = don't be taking neutrals apart if you don't know what's connected to them!So me and my Jman got into a HR box with 2 circuits. He turned off the breakers and undid the joints. There was a load on the neutral when he undid the joint. I put my ticker in the box and was picking up voltage on the neutral. We used a meter and got 230v. This was on the neutral wire that would be continuing downstream, not back to the panel.
What could cause this? Isn't the neutral supposed to have no voltage on it? Just the unbalanced load? Considering that everything is properly bonded at the transformer?