40 volts to switched outlets with the switch off... 120 when switch is on.. what the heck!!!
Testing out units after finish for punch list stuff.Where and what are you measuring 40V off and 120V on?
And did you find that by accident or was there a reason you were looking?
That's what I figured. But it still weirded me out.To me it's a non issue.. probably some induced voltage on the conductor. If it could move a wiggy or light up a bulb, I'd be trying to figure it out.
Is this a high rise with conductors all together in conduit?