300.34 is in Part II of Article 300 and only applies to "over 600 volts".
In general there are no bending rules for conductors under 600 volts in the NEC. There maybe manufacturer's instructions that could be enforced via 110.3(B).
1 - 1 of 1 Posts
This is an older thread, you may not receive a response, and could be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to professional electricians, contractors, and apprentices for residential and commercial work. Come join the discussion about trade knowledge, tools, certifications, wiring, builds, scales, reviews, accessories, classifieds, and more!